Mobile personal protection device of the latest generation. For safe power consumption at unknown sockets. Avoid electrical accidents!
The Mobile latest generation personal protection device.
With peace of mind!
Anyone who wants to use an electrical outlet of an existing electrical installation for commercial purposes must take appropriate protective measures in advance. PRCD‑S pro meets this requirement.
Mit dem Laden des Videos akzeptieren Sie die Datenschutzerklärung von YouTube. Mehr erfahren
With the PRCD‑S pro, it makes no difference whether users wear gloves or not, thanks to the latest electronics.
Fault-free switching on is possible at all times under all operating conditions.
Determining the quality of the protective earth resistance
The PRCD‑S pro not only detects whether the protective earth PE is connected, but also determines its quality. Switching on is only possible if the resistance of the protective earth RPE is less than 1kΩ ist.
Thus, the PRCD‑S meets the highest safety requirements.
The PRCD‑S pro monitors itself. The classic test button is omitted.
Functional test of the residual current circuit upon every connection to the socket and every 2 hours of operation – without interruptions
Relay contact test upon each switch-on and switch-off process
Monitoring of the resistance of the protective earth RPE
Indication of the device status and fault signalling using integrated LEDs
Detection of smooth DC fault currents
Electrical loads and equipment can generate smooth DC fault currents.
If these are connected to an electrical circuit with a Type A fault current circuit breaker, these smooth DC fault currents cause the fault current circuit breaker to not function.
The PRCD‑S pro detects smooth DC fault currents > 6 mA safe!*
*depending on the type of device
DGUV 203–006 konform
DGUV Information 203–006 (DGUV – German Social Accident Insurance) requires the use of appropriate protective measures when connecting electrical equipment to unfamiliar sockets, e.g. use of a portable residual current device according to DIN VDE 0661: